Capstone MicroTurbine C200 Heat Recovery Module (HRM) User’s Manual
| || |
Capstone Turbines Available (new surplus and used)
We buy and sell Capstone Turbine: C30, C60, C65, C200, and C1000. Complete listings. We also offer buying services so you know before you buy. Let us help you make an educated buying decision if you're buying from Ebay or Salvex. Global Energy has been trading Capstone Turbine since 2001.
Publication Title | Capstone MicroTurbine C200 Heat Recovery Module (HRM) User’s Manual
hrm-heat-recovery-ichp Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on: Capstone Turbine Publications | Return to Search List
Search Completed | Title | Capstone MicroTurbine C200 Heat Recovery Module (HRM) User’s Manual
Original File Name Searched: 400021B_HRM_UM.pdf | Google It | Yahoo | Bing
Previous Page | Next Page
Page | 026
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Capstone MicroTurbine C200 Heat Recovery Module (HRM) User’s Manual
Table 4. Diagnostic Messages (Continued)
Prompt Description Corrective Action
The thermocouple sensor is in imminent danger of burning out. This error message will also appear if the resistance of the wires between the thermocouple and the controller is greater than 180 ohms.
Contact your Capstone ASP to check wiring and thermocouple.
Current Output 1 is less than 3.5 mA. Indicates open circuit between controller and modulating actuator.
Contact your Capstone ASP to check wiring.
400021 Rev B (October 2012)
Page 26 of 26
Capstone reserves the right to change or modify, without notice, the design, specifications, and/or contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Search Contact: email@example.com